by Ty from Carrollton, TX 75006
Joseph was very hard working and easy to accommodate. We're still not absolutely certain that the air conditioner is fully repaired and he asked me to keep an eye on it over the next few days and call him if it doesn't cool adequately. Temperature read 60 and he stated it should be reading in the 40s. Joseph thought it might have needed condenser filters changed and I hope this doesn't mean another charge and another day of work missed, I would have liked to have known this before he put everything back together. He made sure we had the right part, explained the parts to me that were being replaced and worked quickly.